Rate your purchase of the IC693CMM321 Rated 4.7/5 based on 18 ratings.
GE Intelligent Platforms / GE Fanuc Series 90-30
SKU 2172041 UPC 0186097397077
?The Ethernet Interface TCP/IP Module? - IC693CMM321. You are able to connect the PLC to an Ethernet network. Transfer data to the PLC from a varied device. Communicate to other devices as much as 16 server connections. Interface with additional GE Fanuc
Ethernet Interface TCP/IP Module
PLC to an Ethernet network
Initiate transfer of data to the PLC
Communicate simultaneously to multiple devices
Interface with other GE Fanuc devices
Communicate from a Host computer
Troubleshooting and Product Information for IC693CMM321
Download product information, troubleshooting guides and operation manuals to get your PLC operational.
The IC693CMM321 is an Ethernet Interface TCP/IP Module. This allows you to connect the PLC to an Ethernet network, transfer data to the PLC from a varied device, communicate to other devices (with up to as many as 16 server connections), and interface with additional GE Fanuc.
What rack size can I use for the IC693CMM321?
You can use any rack size for this product.
What IP address should I use when trouble shooting IC693CMM321?
You should make sure to use an IP address that's above anything else that could be working within your network so it does not conflict with anything else. And, more importantly, so you don't get a returned ping that you are actually testing something other than the intended CMM321.
When testing the 10 Base T port with an Ethernet cable, how will I know that IC693CMM321 is responding?
The LAN LED light will start blinking and you will know IC693CMM321 is ready for testing.
How do I know IC693CMM321, upon testing, is working correctly?
You will get an immediate response that says "reply from" followed by the address you have selected.
When testing the AAUI port, how will I know that IC693CMM321 is responding?
The LAN LED will start blinking and you will get an immediate response, just like with the 10 Base T port.
If IC693CMM321 is not responding, what is my next step?
If IC693CMM321 is not responding, please visit our repair page for this product.
What power supply is required for IC693CMM321?
IC693CMM321 requires Power Supply IC693PWR321 (Rev. K or later), IC693PWR322, or IC693PWR330.
Does this version's hardware require an AAUI transceiver for operation on 10 Base T networks?
No, it does not.
When did the IC693CMM321 come out?
The 9030 series came out in 1988.
For more information on the IC693CMM321 Module of the GE 90-30 Series, please see the Datasheet Manual.
The IC693CMM321 Ethernet Interface TCP/IP
The IC693CMM321 is an Ethernet Interface TCP/IP module. This allows you to connect the PLC to an Ethernet network, transfer data to the PLC from a varied device, communicate to other devices (with up to as many as 16 server connections), and interface with additional GE Fanuc. See specifications on IC693CMM321's website page.
Troubleshootinginformation is available on IC693CMM321’s website page; it also includes a datasheet user-manual and a wiring diagram.
Price and Availability for IC693CMM321
Price for IC693CMM321 module is available by calling 1-800-360-6802 or by filling out our "fast quote".PDF Supplyhas over 30 years of experience with PLCs and has experience with the GE Fanuc 90-30 Series dating back to 1988. IC693CMM321 comes with a minimum 1 year PDF Supply warranty. Returns are accepted for most unopened items. It does require pre-approval and RMA.
Repair your IC693CMM321
PDF Supply canrepairyour IC693CMM321 in 3-5 business days. And PDF Supply stands by all of its repairs with a 2 year customer satisfaction warranty.
Do you have questions or comments?We would love to hear from you!