GE / IP FANUC Series 90/30 In Stock
Other Available Revisions for the IC600BF805 IC600BF805AIC600BF805BIC600BF805CIC600BF805DIC600BF805EIC600BF805FIC600BF805GIC600BF805HIC600BF805IIC600BF805JIC600BF805KIC600BF805LIC600BF805MIC600BF805NIC600BF805OIC600BF805PIC600BF805QIC600BF805RIC600BF805-RRIC600BF805SIC600BF805TIC600BF805UIC600BF805VIC600BF805WIC600BF805XIC600BF805YIC600BF805Z
230Vac/dc Input Module (8 points) GE Fanuc Series Six Board with Face Plate IC600BF IC600B
The GE Fanuc IC600BF805 AC/DC input module has an input voltage of 230 Volts AC/DC. It is a Series Six module with 8 input points and a faceplate and a circuit board that combine to form a complete module assembly. The module is mounted in the I/O rack or I/O rack section of the CPU in a PLC. The I/O rack offers backplane signals and regulated DC power from the power supply and it comes in 3 versions, including high-capacity DC power, high-capacity AC power, and standard AC power. The total current level that is being supplied from the power source makes the difference in the rack requirements. Standard I/O racks offer sufficient current to the modules for most applications. If an application needs I/O modules with current ratings exceeding 6.1 Amps, then a high-capacity I/O rack should be used.
When installing the IC600BF805 AC/DC input module, the users must follow the right sequence of steps. First, set the switches for Dual-In-Line-Package (DIP) at the back of the card slot on the rack backplane to create the right connection or compatibility between the IC600BF805 AC/DC input module and a group of 8 input numbers in sequence in the user program. Second, use the insertion or extraction tool that comes with the Series Six CPU to remove or insert the IC600BF805 AC/DC input module in the card slot. Third, line up the faceplate on top of the circuit board, ensure that the terminals are mated, and then use the thumbscrews to secure the faceplate at the bottom and top of the rack. Fourth, connect the user circuit appropriately. Lastly, line up the terminal cover on the top of the terminal block and slide the terminal cover into place.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.