GE / IP FANUC Series 90/30 In Stock
SKU 2177150 UPC 086430718784
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to indicate any affiliation with or authorization by any rights holder.
Interrupt Input Module (8 points) GE Fanuc Series Six Board with Face Plate IC600BF IC600B
The GE Fanuc IC600BF808 input module is an interrupt input module for GE Series Six PLCs. The IC600BF808 input module allows the users to initiate subroutine execution through the activation of an input. Additionally, a subroutine can also be activated through a user program function. A subroutine, according to the GE Series Six standards, is a program which is separate from the main program and it is only executed when required. One IC600BF808 module can be supported by a GE Model 600 or Model 60 CPU. The IC600BF808 input module can be installed in either a CPU I/O station or in a local I/O station. A total of 8 inputs are available on the IC600BF808 input module and they are divided into 4 groups of 2 inputs each. Each group has its own isolated neutral point.
One LED is also provided for each input on the IC600BF808 input module to indicate the flow of current. The input circuits on the IC600BF808 input module can respond to both falling-edge and rising-edge transitions. Interrupts corresponding to the module inputs are serviced by the system CPU on a first-come, first-serve basis. When multiple interrupts occur at the same time, the interrupt with the lowest number is serviced first. The IC600BF808 input module features 300-microsecond input filtering. Applications for the module include position control, high-speed packaging, and emergency stop applications. The dimensions of the circuit board and the faceplate on the IC600BF808 input module are 208 x 280 x 31 millimeters and 317 x 30 millimeters, respectively. The GE Series Six PLC should be powered off before installing or removing the IC600BF808 module. A single parity error could occur at any address in the system I/O structure if the PLC is not powered down as recommended by GE Fanuc.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.