GE / IP FANUC Series 90/30 In Stock
PDF Supply Company, LLC is not an authorized distributor for GE Fanuc Emerson
Other Available Revisions for the IC600YB817 IC600YB817AIC600YB817BIC600YB817CIC600YB817DIC600YB817EIC600YB817FIC600YB817GIC600YB817HIC600YB817IIC600YB817JIC600YB817KIC600YB817LIC600YB817MIC600YB817NIC600YB817OIC600YB817PIC600YB817QIC600YB817RIC600YB817-RRIC600YB817SIC600YB817TIC600YB817UIC600YB817VIC600YB817WIC600YB817XIC600YB817YIC600YB817Z
Type B Thermocouple Input Module (8 points) YB817 Module Without Face Plate IC600 IC600YB
The IC600YB817 Thermocouple Input Module is a Type B microprocessor-based input module manufactured by GE Fanuc. It comes with 8 electrically isolated inputs that can detect the signals which come from thermocouple devices. It is designed in a way that simplifies troubleshooting. The IC600YB817 Thermocouple Input Module senses lower level analog input values from the thermocouple module and converts them to compatible values for use with the GE Series Six PLCs. The calibration of the module must be done every 6 months to meet the accuracy and efficiency requirements of the system. Some of the features of the input signal conditioning of this module include isolation, filtering, and low-level input signal conditioning.
The IC600YB817 Thermocouple Input Module uses the 2’s complement format to transfer the temperature data to the GE Series Six CPU. This Type B input requires 2.782 to 13.814 MV. The module accuracy rating is 3 degrees Celsius within its thermocouple temperature range 750 to 1820 degrees Celsius. The 5 Volts DC of voltage and 1.7 Amps of current that are required to power the module are provided by the I/O rack power supply. The IC600YB817 Thermocouple Input Module must be installed in a Model 60 CPU rack or I/O rack. It is recommended to install the dual in-line package switches in the back card slot of the rack backplane. Before wiring the module, make sure to follow ANSI standard color codes and thermocouple polarities. During calibrations, the offset potentiometer must be adjusted to obtain the 0 Volts reading, and the gain potentiometer must be calibrated to obtain the 4 Volts reading on the voltmeter.
PDF Supply Company, LLC. sells surplus and refurbished products, which are sourced through independent channels. All warranties and support, if applicable, are with PDF Supply Company, LLC. and not the manufacturer; manufacturer warranties do not apply. PDF Supply Company, LLC. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturers on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. PDF Supply Company, LLC. does not sell or license software that may be needed to operate certain hardware and customers must obtain any necessary software licensing, maintenance, or upgrades from the manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.