GE / IP FANUC Series 90/30 In Stock
SKU 2177415 UPC 02406472990110
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to indicate any affiliation with or authorization by any rights holder.
GENIUS Genius Block (EBA Only) IC660EBA IC660EBA IC660EBA IC660EBA IC660EBA IC660EBA
The GE Fanuc IC660EBA027 input block electronic assembly is an electronic assembly for the Genius I/O system. The IC660EBA027 Genius I/O block electronic assembly is supplied as an assembly for a 24 Volts DC I/O block (BBA027) and it connects to a terminal base assembly (TBA027), which forms the base for I/O the block and provides connection points for the bus cable, field devices, handheld monitors, and the EEPROM. The I/O block is an intelligent, self-sustained, and software configurable device with built-in advanced diagnostics and programmable functionalities. It helps interface a wide range of GE Fanuc discrete, analog input devices to the Genius I/O Bus. The IC660EBA027 electronic assembly is DC-powered with an operating range between 18 and 56 Volts DC (24/48 Volts DC nominal) and a maximum power dissipation rating of 12 Watts.
Structurally, the IC660EBA027 block electronic assembly is made of cast aluminum and every individual component in the assembly comes with open design and thus will require protective enclosures. Unlike the Genius I/O modules which are rack-mounted, the IC660EBA027 electronic assembly can be mounted virtually anywhere and it can be mounted up to 750 meters away from the PLC. The IC660EBA027 electronic assembly’s analog input block is backwards-compatible with older versions and it can be used to replace them. The input block can be configured using a handheld monitor, and its advanced diagnostics provide fault messages (high alarm, low alarm, open wire, over-range, and under-range messages), which can be cleared with the handheld monitor or a CPU. The IC660EBA027 electronic assembly can be replaced without affecting the field-wiring or reconfiguring the whole block. Make sure to turn off the power before removal.
The final letter in the part number (ex. IC660EBA027K) indicates the revision. Revision K or later use the newer style electronic housing and therefore needs the newer style plastic door and may indicate some compatibility issues with the terminal strip.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.