GE / IP FANUC Series 90/30 In Stock
PDF Supply Company, LLC is not an authorized distributor for GE Fanuc Emerson
Other Available Revisions for the IC660EBA100 IC660EBA100AIC660EBA100BIC660EBA100CIC660EBA100-CAIC660EBA100DIC660EBA100EIC660EBA100FIC660EBA100HIC660EBA100KIC660EBA100LIC660EBA100MIC660EBA100NIC660EBA100PIC660EBA100-RR
The IC660EBA100 module is a GE Fanuc Input / Output module with 4 inputs and 2 outputs. It comes with 2 block versions. We have a 115 VAC input/output block and a 24/48 VDC voltage / current block. Each circuit on the 4 input / 2 Output Analog Block, can deliver signals in the following analog ranges:
-10V DC to +10V DC
-5V DC to +5V DC
0-5 V DC
0 -10 V DC
4-20 mA/1-5 volts DC
Due to this flexibility in the above signal ranges, the module blocks can be used in wide arrays of both output and input devices.
You’ll notice LED indicators on the block for indicating how the block is running. If a block develops a fault, the OK LED blinks to give a sign of an existing fault. For certain faults, the block takes preemptive measures by cutting off the module’s output to avert hazardous incidences that could lead to further damage. This input / output module is mountable in any position. For ample heat dissipation, vertical mounting is preferred.
It is recommended that about 1.5 inches are left open between the blocks and 3 inches above and below each block. This facilitates easier removal of the block’s electronics component and provides more space for wiring especially where wires are bundled together.
If mounted in an enclosed area, it’s crucial to leave adequate space for cooling. Remember, overheating is potentially harmful to electronic components. Connections to the I/O blocks are made using Belden 9182 cables. For configuration, a hand-held monitor is attached to the block and powered on. This is followed by a series of configuration prompts. Finally, a device number is assigned to the I/O block to start configuration.
During field wiring, the I/O block is operated using a standard screwdriver for fastening and unfastening the screws. Each terminal can accommodate one AWG #12 or two AWG #14 wires. The minimum wire size that is recommended is AWG #22. Take note that unshielded wire ends do not exceed 2 inches.
The final letter in the part number (ex. IC660EBA100K) indicates the revision. Revision K or later use the newer style electronic housing and therefore needs the newer style plastic door and may indicate some compatibility issues with the terminal strip.
PDF Supply Company, LLC. sells surplus and refurbished products, which are sourced through independent channels. All warranties and support, if applicable, are with PDF Supply Company, LLC. and not the manufacturer; manufacturer warranties do not apply. PDF Supply Company, LLC. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturers on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. PDF Supply Company, LLC. does not sell or license software that may be needed to operate certain hardware and customers must obtain any necessary software licensing, maintenance, or upgrades from the manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.