GE / IP FANUC Series 90/30 In Stock
|Product Type||Hand-Held Monitor|
|Required AC Power||115 to 230V AC|
|Frequency||47 to 63 Hz|
|Fully Charged Battery Operation||6 hours|
|Display Languages||English, German, French, Italian|
|Operating Temperature||32 to 140 degrees Fahrenheit|
|Dimensions||10.85 x 4.30 x 2.25 inches|
GE Fanuc’s IC660HHM501 Hand-held Monitor (HHM) is an interface operating device used to set up, monitor, and configure a Genius I/O and communication system. The HHM can be used as a portable monitoring device if desired by the user. Included in the IC660HHM501's features is a four-lined LCD display with 16 characters each, language selection display (English, Spanish, French, and Italian), a 20-key sealed membrane keypad, and a keyswitch limits access to operations of certain functions of the device. The ability to communicate with the I/O blocks and force discrete and analog I/O is the primary feature of the HHM, even in the absence of a PLC or computer connected to the bus.
Data for the Genius bus and all its devices are displayed on the screen of the IC660HHM501 to help the user receive and review I/O data for any device on the bus, memory data from CPUs, global data addresses, bus scan time, diagnostics, and descriptions of all devices on the bus. Operating from its battery pack or AC power, the IC660HHM501 handheld monitor has a required 115/230 VAC at 15% or 47-63 Hz of AC power for the battery charger. Even if using AC power, a battery pack must be installed. Full charge takes approximately six hours. For power conservation, the HHM has an automatic shutoff time of 10 minutes. When continuous operation is required, this feature can be disabled.
The monitor independently weighs 1.6 lbs. and its size is 8.00” x 3.75” x 1.25”. If stored in its protective case, the IC660HHM501 weighs 1.8 lbs. and measures 10.85” x 4.30” x 2.25”. The HHM can be permanently installed using a panel mounting kit and should be installed with access to 115 VAC or 230 VAC power. The acceptable operating temperature range is zero to 60C (32-140F), with a storage temperature range of -40 to +70C (-40 to 158F). Non-condensing humidity should not drop below 5 percent and should not rise above 95 percent.
Repair your IC660HHM501
Adding 75 Ohm Resistor When Receiving Communication Errors
Description: The current release have an impedance that is higher than previous releases.
Resolution: To help with this condition disconnect the Block from the Genius Bus and add a 75 Ohm carbon resistor between serial 1 and serial 2. DO NOT USE WIRE WOUND RESISTORS!
For more information on the IC660HHM501 Hand Held Monitor of the GE Fanuc Genius I/O Series, please see the Datasheet User-Manual.
IC660HHM501 is a Phase B GE Genius block and is compatible with all GENIUS supported PLC systems. The earlier version- IC660HHM500 is a Phase A GE Genius Block and is only compatible with Series Six and Series Five PLCs.
The final letter in the part number (ex. IC660HHM501K) indicates the revision. Revision K or later use the newer style electronic housing and therefore needs the newer style plastic door and may indicate some compatibility issues with the terminal strip.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.