GE / IP FANUC Series 90/30 In Stock
SKU 2175454 UPC 0797801131513
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to indicate any affiliation with or authorization by any rights holder.
GENIUS Terminal Assembly for (TPM Only) TPM100 for IC660BPM100 IC660T IC660TP IC660TP
The IC660TPM100 module by GE Fanuc is an I/O module that is used in industrial automation applications. It offers out-of-the-box performance and it comes in a compact size. It saves panel space in the PLC system. This terminal assembly runs with a voltage rating of 115 to 230 Volts AC or 125 Volts DC. It is fully compatible with the GE IC660BPM100 power monitoring block. This monitoring block lets the users monitor the flow of power through the PLC system. The I/O module helps the monitoring block to measure current, voltage, and different factors during the operation process. The IC660TPM100 module can be used with both 3-wire and 4-wire systems. This module can be replaced and installed inside the monitoring block that hosts it. The monitoring block should be disconnected from the power and properly grounded during the installation process.
The IC660TPM100 module fits perfectly with the power monitoring block by GE that can measure the RMS value of the voltage, current, VARs, and distorted waveforms. It offers simple user connections. It also helps to indicate the magnitude of the system harmonic content. The power monitoring block has the ability to work with as many as 3 transformers at a time, including a neutral current transformer. It can be connected to a handheld monitor. The IC660BPM100 module is designed with an open enclosure and it has no IP rating for water resistance. The module is installed inside the power monitoring block and it should be handled carefully. The ambient temperature should be maintained between 0 and 60 degrees Celsius for operation. When not in use, the module can be stored in a clean and dry place with no contaminants in the atmosphere.
The final letter in the part number (ex. IC660TPM100K) indicates the revision. Revision K or later use the newer style electronic housing and therefore needs the newer style plastic door and may indicate some compatibility issues with the terminal strip.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.