GE / IP FANUC Series 90/30 In Stock
IC694BEM321 is a PACSystems RX3i master controller module that provides an I/O Link communications with up to 16 slaves if needed. This module acts as a master on a proprietary GE I/O Link. The master in the setup can receive 1024 discrete inputs from slaves and send up to 1024 discrete outputs.
The module can be installed on any available I/O slot in the RX3i or Series 90-30 system. However, for the best overall performance, it should be installed in the main backplane or in an expansion backplane. The availability of the power supply will determine the maximum number of I/O links that can be installed. If multiple I/O link master modules are in the same PLC system, then they must be placed on separate I/O links to operate.
A fuse protects the +5 volt signal pins that are used by the Optical Adapter cable and is replaceable by a 0.5A fast-blow fuse if needed. This module has three separate LEDs that show both communicating and operating status. The Link Restart pushbutton is available to restart the operation of the link if failure occurs; however, pushing the Link Restart while the link is operating has no effect on the system. If a failure does occur, all slaves must be power cycled before using Link Restart. The IC694BEM321 has a front module with one 20 pin Honda-type connector. This is used for the connection to the first slave on the I/O link. All signals are RS422/485 compatible on this unit.
|Module Type:||I/O Link Interface|
|Number of Slots:||1 (single slot)|
|Backplane Support:||Universal Backplane|
|I/O Points:||Up to 1024 inputs and 1024 outputs|
|Communication Ports:||(1) RS485/422|
|LEDs||OK, ACTV, CFG|
Module type PACSystems RX3i controller module, providing I/O Link communications with up to 16 I/O Link slaves.
I/O Points Up to 1024 inputs and 1024 outputs
+5Vdc current required without Optical Adapter connected: 415mA
with Optical Adapter: 615mA
â–ª PACSystems RX3i CPUs
â–ª Series 90-30 CPUs (models 311, 313, 321, 323, 331, and 341): release 4.4 or later, and all versions of the CPU models 350, 351, 352, 360, 363, and 364
â–ª Series 90-30 Hand-held Programmer (HHP)
Troubleshooting information is available on IC694BEM321's website page; it also includes a datasheet user-manual and a wiring diagram.
Repair your IC694BEM321
For more information on the IC694BEM321 I/O Link Interface Master Module of the GE Fanuc RX3i Series, please see the Datasheet User-Manual.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.