GE / IP FANUC Series 90/30 In Stock
PDF Supply Company, LLC is not an authorized distributor for GE Fanuc Emerson
IC693BEM341 is a FIP Bus Controller with feature supporting mode 30. Manufactured by GE Automation and Controls, it also supports the 2.5Mhz variant version of (IC693BEM341) Bus Controller. It is identical in functionally to the other versions, only the network speed t differs. The requirements of CPU state for 2.5Mhz variant version (IC693BEM341) bus controller to have must install 8.10 version firmware or higher. During configuration, the bus controller needs a HHP (Hand-Held Programmer) with a Release Version 2.0 if not higher. It will also require the IC641CTLxxx programming software for windows which allows for configuring it with the configuration utility FBCLOAD for proper operation of the network. This version is not configurable via the programming software IC641SWPxxx. This version also supports mode 11, mode 20 and mode 30.
There are newly added features and new functions which came with the release of this version of the bus controller. Enhanced display for the HHP operating in all modes which enable the revision firmware to be displayed. Also, the support for time stamping in Boolean Values up till 1024. The mode 30 is newly added to the IC693BEM341 bus controller. This also added new features to the bus controller when in mode 30 such as redundancy, slave device management (drives), slave device monitoring (PLCs, drives, control stations), Boolean value time stamping, services for messaging, synchronous exchange MPS, external configuration reception throughout FIP network. This release also fixed some of the problems faced in previous versions which include FBC module loss in all modes, incorrectly determined state of the application in all modes, incorrectly set input COMVs validity bits in mode 10, incorrectly updated produced COMVs in mode 10, incorrectly received a message for time stamping in mode 20.
|Module Type:||FIP Bus Controller (2.5MHz)|
|Number of Slots:||1 (single slot)|
|Backplane Support:||Universal Backplane|
|Current Consumption:||1.2 Amps Max|
|Communication Ports:||(2) 9-pin male D connectors, (1) RS-485|
Ordering information IC693BEM341
Module type Series 90–30 PLC module, providing FIP communications
with other devices.
Quantity per PLC As power supply will allow
Current consumption 1.2 Amps maximum, 800mA typical
Series 90–30 PLC, memory types for %G, %I, %Q, %AI, %AQ, %R, %M, %T
Software diagnostics Status bits, Fault Reporting to Series 90–30 PLC
Operating temperature 0C to +55C (+32F to +131F)
Storage temperature –25 C to +70C (–13F to +158F)
Humidity 5% to 95% (non–condensing)
Vibration and shock 0.2 inch displacement 5Hz to 10Hz
1 G 10Hz to 200Hz
5 G 10Ms duration
Repair your IC693BEM341
For more information on the IC693BEM341 FIP Bus Controller of the GE 90-30 Series, please see the Datasheet Manual.
PDF Supply Company, LLC. sells surplus and refurbished products, which are sourced through independent channels. All warranties and support, if applicable, are with PDF Supply Company, LLC. and not the manufacturer; manufacturer warranties do not apply. PDF Supply Company, LLC. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturers on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. PDF Supply Company, LLC. does not sell or license software that may be needed to operate certain hardware and customers must obtain any necessary software licensing, maintenance, or upgrades from the manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.