GE / IP FANUC Series 90/30 In Stock
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to in indicate any affiliation with or authorization by any rights holder.
PDF Supply is NOT an authorized distributor for this manufacturer and therefore the manufacturer’s warranty does not apply. Product comes with PDF Supply's 1-year, 2-year, or 3-year warranty.
The GE Fanuc IC693CBL302 is an I/O bus expansion cable specifically for Series 90-30 systems. Also called a wye cable, this one is a particularly special one among the family as it is equipped with a single male connector on either end of the cable. Each male connector is a 25-pin D connector. The head that connects to the expansion baseplate is a terminated male connector. The IC693CBL302 allows the user to extend the I/O Bus to either remote or expansion baseplates within the system. Remember, the IC693CBL302 is designed for Sereis 90-30 systems. If the system requires more I/O slots, or in instances when the baseplates must be located further away from the CPU base plate, a wye cable is necessary.
This 50-foot-long cable also has I/O bus terminating resistors, which are built into the connector at the end of the cable. For that reason, users don’t need to install a separate termination block in their system when they use this cable. In a system with just one expansion baseplate, the user can terminate the I/O bus by using this cable. These termination resistors will terminate the I/O bus. A maximum of seven wye cables may be used in a single I/O expansion system can have at one time. The total cable length must be less than 50 feet (15 meters) between the CPU baseplate and the last expansion baseplate. It is never safe to either connect or disconnect cables when the I/O expansion baseplate is powered on. Always disconnect the baseplate from the power source to connect or disconnect cables, such as the IC693CBL302.
PDF Supply sells used surplus products. PDF Supply is not an authorized distributor, affiliate, or representative for the brands we carry. Products sold by PDF Supply come with PDF Supply’s 1-year, 2-year, or 3-year warranty and do not come with the original manufacturer’s warranty. Designated trademarks, brand names and brands appearing herein are the property of their respective owners. This website is not sanctioned or approved by any manufacturer or tradename listed.
Rockwell Disclaimer: The product is used surplus. PDF Supply is not an authorized surplus dealer or affiliate for the Manufacturer of this product. The product may have older date codes or be an older series than that available direct from the factory or authorized dealers. Because PDF Supply is not an authorized distributor of this product, the Original Manufacturer’s warranty does not apply. While many Allen-Bradley PLC products will have firmware already installed, PDF Supply makes no representation as to whether a PLC product will or will not have firmware and, if it does have firmware, whether the firmware is the revision level that you need for your application. PDF Supply also makes no representations as to your ability or right to download or otherwise obtain firmware for the product from Rockwell, its distributors, or any other source. PDF Supply also makes no representations as to your right to install any such firmware on the product. PDF Supply will not obtain or supply firmware on your behalf. It is your obligation to comply with the terms of any End-User License Agreement or similar document related to obtaining or installing firmware.