GE / IP FANUC Series 90/30 In Stock
SKU 2175056 UPC 0307678148257
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to indicate any affiliation with or authorization by any rights holder.
The "LT" Revision is for the PDF Supply Low Temperature Testing Service. PDF Supply warranty will apply. A $150 service charge will be added at checkout.
The GE Fanuc IC693CMM311 is a Communications Coprocessor Module. This component provides a high performance coprocessor for all Series 90-30 modular CPUs. It cannot be used with embedded CPUs. This covers models 311, 313, or 323. This module supports GE Fanuc CCM communications protocol, the SNP protocol and the RTU (Modbus) slave communications protocol. It is possible to configure the module using the configuration software. Alternatively, users can opt for a default setup. It has two serial ports. Port 1 supports RS-232 applications while Port 2 supports either RS-232 or RS-485 applications. Both ports are wired to the module’s single connector. For this reason, the module has been supplied with a wye cable (IC693CBL305) in order to separate the two ports to make wiring easier.
It’s possible to use up to 4 Communications Coprocessor Modules in a system that has a CPU of 331 or above. This can only be done via the CPU baseplate. In versions before 4.0, this module presents a special case when both ports are configured as SNP slave devices. The ID value –1 in a Cancel Datagram request received at either slave device will end up cancelling all established Datagrams on both slave devices within the same CMM. This is different to a CMM711 module, which has no interaction between datagrams established on the serial ports. Version 4.0 of the IC693CMM311, which was released in July 1996, solved the issue. Older versions of the module that have this problem please contact us for repairs.
|Module Type:||Communications Co-Processor|
|Communication Protocols:||GE Fanuc CCM, RTU (Modbus), SNP|
|Internal Power:||400 mA @ 5 VDC|
|Port 1:||Supports RS-232|
|Port 2:||Supports either RS-232 or RS-485|
PDF Supply Company, LLC. sells surplus and refurbished products, which are sourced through independent channels. All warranties and support, if applicable, are with PDF Supply Company, LLC. and not the manufacturer; manufacturer warranties do not apply. PDF Supply Company, LLC. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturers on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. PDF Supply Company, LLC. does not sell or license software that may be needed to operate certain hardware and customers must obtain any necessary software licensing, maintenance, or upgrades from the manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or other authorized source. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.