GE / IP FANUC Series 90/30 In Stock
SKU 2171467 UPC 0799705795099
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to indicate any affiliation with or authorization by any rights holder.
IC697BEM763 is a high-performance interface module for the 90-70 series designed by GE Fanuc. This part provides automation between series 90-70 PLC systems and GE Drive Systems DLAN / DLAN+ LAN protocols. The IC697BEM763 module allows drives such as AC2000, DC300, and DC2000 to be controlled from series 90-70 programs. The GE Drive system only communicates using DLAN or DLAN+ local area network protocols.
The IC697BEM763 module operates either as a DLAN or DLAN+ controller. It is important to note that a single module cannot be both a DLAN and DLAN+ controller at the same time. In a situation where the application requires both DLAN and DLAN+ devices, two DLAN Interface modules must be used. In a single rack system, the IC697BEM763 module resides in the same rack as the PLC processor. In a multiple rack system, the IC697BEM763 module can reside either in the central processing unit rack or in the expansion racks.
During installation, the CPU power supply unit and the IC697BEM763 module must reside in designated slots within each rack. The CPU module must reside in slot 1 of rack 0. When the IC697BEM763 module system includes a BTM, it can be allocated in any slot as long as it is not on the right side of an empty slot. If the PLC system has more than one rack, the IC697BEM763 module must be located in slot 1 of each expansion slot. Note: IC697BEM763A must be installed on the right side of all the other GE Fanuc modules. There can be no empty slots between the IC697BEM763A and the CPU module.
IC697BEM763 modules can be placed in any unused slot in the appropriate rack. However, all of the slots between the IC697BEM763 module and the PLC CPU must be occupied. If any of these slots are empty, the IC697BEM763 module cannot communicate across the backplane to the PLC CPU.
Repair your IC697BEM763
For more information on the IC697BEM763 DLAN Drive Interface Module for the IC600 PLC of the GE Fanuc 90-70 Series, please see the Datasheet User-Manual.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.