GE / IP FANUC Series 90/30 In Stock
Other Available Revisions for the IC200ALG266 IC200ALG266AIC200ALG266BIC200ALG266CIC200ALG266DIC200ALG266EIC200ALG266FIC200ALG266GIC200ALG266HIC200ALG266IIC200ALG266JIC200ALG266KIC200ALG266LIC200ALG266-LTIC200ALG266MIC200ALG266NIC200ALG266OIC200ALG266PIC200ALG266QIC200ALG266RIC200ALG266SIC200ALG266TIC200ALG266UIC200ALG266VIC200ALG266WIC200ALG266XIC200ALG266YIC200ALG266Z
The IC200ALG266 by GE Fanuc is a TUV approved input module for the Versamax series. It has 15 channels and 15-bit voltage. This analog input module provides an interface to 15 current inputs, which are single-ended and share a common return. The IC200ALG266 is rated for use in SIL2 applications.
The module receives power from the backplane power supply, meaning it does not require any external power source for operation. It is, however, important to note that power for the user’s transceivers must be supplied from an external source. Intelligent processing for this module is possible via the module’s CPU or NIU, which provides intelligent processing to allow 15 words of analog input data.
The IC200ALG266 contains an active circuit that protects the input sense resistors. If an input is accidentally connected to +24V field power, the module holds input current at 40mA max to prevent damage from too much power. Additional protection for the sense resistors is provided by opening the input loop while the module is powered off. When the module is powered off, any connected external transmitters that perform open wire fault detection will see the open input loop as an open wire fault, and any external receivers connected in series with the module will not receive a valid signal.
The module’s LED Indicator turns green when any of the following processes is taking place: when backplane power is present, when internally generated field power is functioning properly, when the module has been configured, and/or when it has been recognized on the backplane.
The IC200ALG266 reports loss of internal power fault for field-side circuits and also reports an open wire fault for each channel when in 4-20mA mode. The module reports an Internal Hardware fault upon detection of an A/D conversion malfunction. The module detects this malfunction by applying a known stimulus to the A/D conversion path and verifying the expected result. Should there be three consecutive occurrences, scanning comes to a stop, the OK LED is turned off, and an Internal Hardware fault is reported. To clear this fault, the module must be power cycled or replaced.
|No. of channels:||15 single-ended, one group|
|Current Range:||4 - 20 mA, 0 - 20 mA|
|Update Rate:||7.5 ms|
|Input Filter Response:||24 Hz +/-20%|
|Power Consumption:||100 mA from +5V bus|
Repair your IC200ALG264
For more information on the IC200ALG266 15-Channel, 15-Bit, Current, TUV Approved, Analog Input Module of the GE Fanuc Versamax Series, please see the Datasheet User-Manual.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.