GE / IP FANUC Series 90/30 In Stock
Other Available Revisions for the IC200BEM003 IC200BEM003-AAIC200BEM003AIC200BEM003BIC200BEM003CIC200BEM003DIC200BEM003EIC200BEM003FIC200BEM003GIC200BEM003HIC200BEM003IIC200BEM003JIC200BEM003KIC200BEM003LIC200BEM003-LTIC200BEM003MIC200BEM003NIC200BEM003OIC200BEM003PIC200BEM003QIC200BEM003RIC200BEM003SIC200BEM003TIC200BEM003UIC200BEM003VIC200BEM003WIC200BEM003XIC200BEM003YIC200BEM003Z
IC200BEM003 is a PLC Network Communications PROFIBUS-DP (Master) Module from the GE Fanuc Versamax Series. This network style master module allows a Versamax CPU005, ProfitNet Scanner, or CPUE05 to receive and send data on a Profibus-DP network. This specific master module features numerous Profibus communication options with support for all standard data rates and sync/freeze modes. With a maximum support of 3,584 bytes of input or output data, the IC200BEM003 supports DP-V1 read, write, and alarm messages with ease. Any necessary firmware updates are received indirectly from the host controller using the WinLoader software utility.
When installing the master module in hazardous areas, make sure to heed all warnings for the given atmosphere, including turning off the power source. Install the module by clicking the communications carrier on the DIN rail, typically on the same section of 35 mm x 7.5 mm DIN rail with conductive, non-painted surface for proper grounding. Install the module on the communications carrier with the latch in the unlock position. Align the connector, latch the post, and press down until the unit clicks into place on both tabs. Once in place, the latch should be moved to the locked position for security.
The user should note that Profibus utilizes a linear bus architecture that requires active bus termination at both ends for proper functionality. Devices in this network connect directly to the bus cable or via sub lines depending on user needs. Once the IC200BEM003 starts, LED indicator lights help show proper functioning.
|Module Type:||Network Master Module|
|Number of Stations:||125 Profibus-DP Slave devices|
|I/O Data:||3584 Bytes of input and output data|
|Network Data Rate:||9.6 Kbaud to 12 Mbaud|
|Power Consumption:||450 mA from 5 V output|
Repair your IC200BEM003
For more information on the IC200BEM003 PLC Network Communications PROFIBUS-DP (Master) Module from the GE Fanuc Versamax Series, please see the Datasheet User-Manual.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.