GE / IP FANUC Series 90/30 In Stock
SKU 2177322 UPC 0500934121388
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to indicate any affiliation with or authorization by any rights holder.
Other Available Revisions for the IC200MDL243 IC200MDL243A/AIC200MDL243B/BIC200MDL243C/CIC200MDL243D/DIC200MDL243E/EIC200MDL243F/FIC200MDL243G/GIC200MDL243H/HIC200MDL243I/IIC200MDL243J/JIC200MDL243K/KIC200MDL243L/LIC200MDL243LT/LTIC200MDL243M/MIC200MDL243N/NIC200MDL243O/OIC200MDL243P/PIC200MDL243Q/QIC200MDL243R/RIC200MDL243S/SIC200MDL243T/TIC200MDL243U/UIC200MDL243V/VIC200MDL243W/WIC200MDL243X/XIC200MDL243Y/YIC200MDL243Z/Z
IC200MDL243 is a VersaMax 120 VAC Discrete Input Module with 16 points. This particular module provides 16 isolated inputs that are positive logic or of the sourcing type. These inputs receive current from AC input devices while the return current is on the common. Each input has an individual and separate return. To power the IC200MDL243, the operation originates in the backplane. The CPU or NIU is the supplier of intelligent processing for the input module. LEDs are standard and display both backplane power and on/off state for each input point.
Isolation of user input to logic and frame ground is 250 VAC continuous or 1500 VAC for one minute with input voltage of 120 VAC nominal or 0 to 132 VAC. On and off state voltage is 70 to 132 VAC and 0 to 20 VAC, respectively, with on and off state current at 5mA minimum and 2.5mA maximum. This module has input impedance of 8.6k Ohms at 60HZ and 10.32k Ohms at 50Hz, both typical.
When installing the IC200MDL243, the user should first check all components for any damage that may have occurred during shipping. If any part of the component is damaged, it should be replaced as damage could affect overall unit performance. The installer should note that no derating is needed for the 16 point modules if mounted vertically (A, B) on the DIN rail. Other forms of mounting will require derating at 132 VAC if mounted horizontally. If hot insertion is done incorrectly, other modules on the backplane can be negatively affected, so proper procedures should be closely followed.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.