GE / IP FANUC Series 90/30 In Stock
SKU 2173135 UPC 0891624231976
All product names, trademarks, brands and logos used on this site are the property of their respective owners. PDF Supply is not an authorized distributor, reseller or representative of the products featured on this website. The depiction, description or sale of products featuring these names, trademarks, brands and logos is for identification purposes only and is not intended to indicate any affiliation with or authorization by any rights holder.
Other Available Revisions for the IC200MDL244 IC200MDL244A/AIC200MDL244B/BIC200MDL244C/CIC200MDL244D/DIC200MDL244E/EIC200MDL244F/FIC200MDL244G/GIC200MDL244H/HIC200MDL244I/IIC200MDL244J/JIC200MDL244K/KIC200MDL244L/LIC200MDL244LT/LTIC200MDL244M/MIC200MDL244N/NIC200MDL244O/OIC200MDL244P/PIC200MDL244Q/QIC200MDL244R/RIC200MDL244S/SIC200MDL244T/TIC200MDL244U/UIC200MDL244V/VIC200MDL244W/WIC200MDL244X/XIC200MDL244Y/YIC200MDL244Z/Z
IC200MDL244 is a VersaMax 240 VAC Isolated Input Module with Eight points. This particular module provides eight discrete inputs that are positive logic or of the sourcing type. These inputs receive current from AC input devices while the return current is on the common. Each input has an individual and separate return. To power the IC200MDL244, the operation originates in the backplane. The CPU or NIU is the supplier of intelligent processing for the input module. LEDs are standard and demonstrate both backplane power and on/off state for each input point.
Isolation of user input to logic and frame ground is 250 VAC continuous or 1500 VAC for one minute with input voltage of 240 VAC nominal or 0 to 264 VAC. On and off state voltage is 155 to 264 VAC and 0 to 40 VAC, respectively, with on and off state current at 7mA minimum and 1.5mA maximum. This module has input impedance of 38.5k Ohms at 60HZ and 46.3k Ohms at 50Hz, both typical.
When installing the IC200MDL244, the user should first check all components for any damage that may have occurred during shipping. If any part of the component is damaged, it should be replaced as damage could affect overall unit performance. When installing, wiring diagrams may be found online. The installer should note that these modules should only be used with compact terminal style carriers or a terminal style carrier. The use of a connector style carrier is not approved for this module type due to higher isolation requirements. If hot insertion is done incorrectly, other modules on the backplane can be negatively affected, so proper procedures should be closely followed.
PDF Electric & Supply Inc. sells new, new surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with PDF Electric & Supply Inc. and not the manufacturer. PDF Electric & Supply Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. The products listed on this website may vary as to their country of origin; the accessories, and other items included with the product; and the language used on the packaging, the parts, and any related instructions or printed material related to the products. This website is not sanctioned or approved by any manufacturer or tradename listed. Designated trademarks, brand names and brands appearing herein are the property of their respective owners.