GE / IP FANUC Series 90/30 In Stock
Troubleshooting Guide for the GE Series 90-30 PLC System.
The GE Fanuc Series 90-30 PLC System has the largest installed base of all GE PLC's, therefore we felt it was important to assist users with some troubleshooting procedures.
Our 33 years of expertise allows us to provide a concise process for identifying problems, as well as procedures which will help you recover from a factory-down situation.
There's an old saying - "If you don't know where you're going, then any road will take you there."
This guide will help you identify the PLC problems, and then systematically provide you with practical solutions.
The very first step to understanding the GE Series 90-30 PLC status is to inspect the four LED's on the front of the power supply. When the green LED power LED is on, it indicates that all power in and out of the power supply appears to be functional.
If this LED is off, install a battery on the front of your CPU to maintain the program, and then simply replace the power supply.
Note: The Series 90-30 has 8 different power supply modules. See all the modules here.
The green 'OK' LED indicates that the CPU appears to pass its power-up test. If this LED is off, then replace your CPU. There is most likely a hardware fault in the CPU module.
Note: The Series 90-30 has 17 CPU modules. See all the modules here
The green 'RUN' LED indicates that the CPU is in run mode and is solving program logic properly. if this LED is green, your problem most likely lies with the failed devices such as I/O modules, and not the PLC system.
If this LED is off, we will walk you through troubleshooting later in this guide.
Finally, the red 'BATT' LED should be off, which indicates that your battery is good. If the red LED is on:
The most common failure of the GE Series 90-30 is the 'RUN' LED is off, which generally indicates that an incident has forced the CPU out of 'RUN' mode.
Connect your programming unit to the RS-485 Serial Port on the power supply, and then navigate to the fault tables in your programming software.
There are two basic fault tables; I/O and CPU. There, you will find time and date stamp faults that have caused your system to exit 'RUN' mode.
In many cases, it will identify rack and slot positions of a failed module. Once you have fixed the issue creating the fault, clear the fault tables so that any additional faults will be logged at next power up. Continue this process until your Series 90-30 PLC System is back up and running.
We hope our troubleshooting guide has helped you track down the problem in your PLC system.
Should you to need to repair or replace any parts for your GE Fanuc 90-30 PLC, please contact us at 1-800-360-6802 or visit our website at www.pdfsupply.com
PDF Supply sells used surplus products. PDF Supply is not an authorized distributor, affiliate, or representative for the brands we carry. Products sold by PDF Supply come with PDF Supply’s 1-year, 2-year, or 3-year warranty and do not come with the original manufacturer’s warranty. Designated trademarks, brand names and brands appearing herein are the property of their respective owners. This website is not sanctioned or approved by any manufacturer or tradename listed.
Rockwell Disclaimer: The product is used surplus. PDF Supply is not an authorized surplus dealer or affiliate for the Manufacturer of this product. The product may have older date codes or be an older series than that available direct from the factory or authorized dealers. Because PDF Supply is not an authorized distributor of this product, the Original Manufacturer’s warranty does not apply. While many Allen-Bradley PLC products will have firmware already installed, PDF Supply makes no representation as to whether a PLC product will or will not have firmware and, if it does have firmware, whether the firmware is the revision level that you need for your application. PDF Supply also makes no representations as to your ability or right to download or otherwise obtain firmware for the product from Rockwell, its distributors, or any other source. PDF Supply also makes no representations as to your right to install any such firmware on the product. PDF Supply will not obtain or supply firmware on your behalf. It is your obligation to comply with the terms of any End-User License Agreement or similar document related to obtaining or installing firmware.